This application note covers the retrofit of a Comm/net systems battery rack alarm wiring for connection to the System Interface Card of Emmerson NetSure 721 power plant for breaker trip monitoring. For the complete procedure open the attached PDF.
016-1802-10: Hot Jumper Kit for Battery Rack Alarm Wire ( 1 Kit per bay is required)
Wire Crimper for 18 AWG connectors
Sockets or wrenches
18 AWG Wire
Diagram 1: Alarm connection one line
If you are experiencing problems, please contact Comm/net Systems Support
Comm/net Systems Inc. Support
or submit a support ticket through this portal.